It is a digital temperature controller module.LCD display, very clear, easy to use, powerful.It can be widely used at Smart home,Industrial control,Automatic irrigation,Indoor ventilation.Protection equipment.
2>.Power-down memory function;
3>.Emergency stop function;
4>.Real-time display temperature;
5>.Automatically save parameters;
6>.Support UART Set;
7>.Support Heating and Cooling work mode;
8>.High temperature buzzer alarm;
9>.Work status indicator;
10>.Independent of parameters;
11>.With case, beautiful and practical;
13>.Multiple parameters are displayed simultaneously.
1>.Product Name:Digital Temperature Controller
3>.Working Voltage:DC 6V-30V
4>.Control Load Current:10A(Max)
5>.LCD refresh rate:0.5 second
6>.Temperature Sensor:NTC-10K B3950
7>.Test temperature: -50~110℃
9>.Sensor length: 0.5 meter
10>.Sensor probe specifications:4*30mm Stainless steel
1>.’ H ’: Heating mode.
Relay will turn ON and the heating device starts to work when Current Temperature Value is less than Setting Temperature Value - Return Temperature Value.
Relay will turn OFF and the heating device stops to work when Current Temperature Value is more than Setting Temperature Value.
2>.’ C ’: Cooling mode.
Relay will turn ON and the cooling device starts to work when Current Temperature Value is more than Setting Temperature Value + Return Temperature Value.
Relay will turn OFF and the cooling device stops to work when Current Temperature Value is less than Setting Temperature Value.
3>.’ OPH ’: ON/OFF delayed start.
The system starts timing 'T' when a normal heating or cooling operation is completed.The system will begin the next round of heating or cooling only after 'T'>'OPH'.
4>.’ OFE ’: Temperature correction function(-10.0~10.0℃).
If the module works for a long time, there may be deviations. Corrected by this function.
Actual Temperature Value = Current Temperature Value + Calibration Value.
5>.’ ALA ’: Set high temperature alarm.
Module will turn on the sound and light alarm and relay will OFF at the same time when Current Temperature Value is more than Set Alarm Temperature Value.Any button to stop the sound and light alarm.
1>. Set or read data by UART.
The parameters such as start temperature, stop temperature, temperature correction, etc. can be set through the UART.
2>.Temperature real-time reporting.
The module transmits the detected temperature to the terminal through the UART at intervals of 1 s to facilitate data acquisition if the temperature reporting function is turned on.
3>.Relay enable (default on).
If the relay enable is turned off, the relay remains off.
That is, the output state will never change, no matter what the measured temperature is.
Press button ‘STOP’ and ‘SET’ for more than 3second at the same time to restore the factory settings.
Long press:keep press button for more than 3second.
1>.Set Working mode/Setting temperature/Return Temperature Value
1.1>.Short press button 'SET' and enter the quick setting interface;
1.2>.Switch the parameters that need to be set for Working mode/Setting temperature/Return Temperature Value by short press button 'SET'.
1.3>.Modify the parameter value by button 'UP' or 'DOWN' after select parameter.Support short press/long press;
1.4>.Exit the quick setting interface and save the parameters by long press button 'SET' for 3second or continue 6S without any button operation.
NOTE:The Return Temperature Value display in the first line where the Current Temperature Value display position.
The Setting Temperature Value display in the second line after ‘H’ or ‘C’.
2.1>.Long press button 'SET' and enter the parameter setting interface.
2.2>.Switch the parameters that need to be set for OPH/OFE/ALA by short press button 'SET'.
2.3>.Modify the parameter value by button 'UP' or 'DOWN' after select parameter.Support short press/long press;
2.4>.Exit the parameter setting interface and save the parameters by long press button 'SET' for 3second or continue 6S without any button operation.
2.5>How to turn on the high temperature alarm ‘ALA’ (default off).Select ‘ALA’ interface,short press button ‘STOP’ to ON or OFF ‘ALA’.Set high temperature value by button ‘UP’ or ‘DOWN’ if turn ON ‘ALA’.If the high temperature alarm function is turned OFF, ‘ALA’ displays ‘----’ as a reminder.LCD will display ‘W’ if turn ON ‘ALA’.
2.6>.How to enable delayed start ‘ OPH ’(default off).Select ‘ OPH ’ interface,short press button ‘STOP’ to ON or OFF ‘ OPH ’.Set delay time value by button ‘UP’ or ‘DOWN’ if turn ON ‘ OPH ’.If the delayed star function is turned OFF, ‘ OPH ’ displays ‘----’ as a reminder.LCD will display ‘h’ in last line and last bit if turn ON delayed start.
1>.Connect NTC sensor to Digital Temperature Controller;
2>.Connect voltage to module;
4>.Remove input voltage;
5>.Connect to load;
6>.Connect voltage to module;
UART Communication and Parameter Settings:
The system supports UART data upload and parameter setting functions (TTL level);
UART: 9600, 8, 1
|1||start||Start temperature report|
|2||stop||Stop temperature report|
|3||read||Read setting parameters|
|4||on||Relay enable ON|
|5||off||Relay enable OFF|
|7||B:XX.X||Set Return Temperature Value (00.0~30.0℃)|
|8||OFE:XX.X||Temperature calibration (-10.0~10.0℃)|
|9||ALA:XX.X||Alarm temperature (-50.0~110.0℃)|
|10||OPH:XXXX||Delayed start time (0~9999minutes)|
1>. Smart home
2>. Industrial control
3>. Automatic irrigation
4>. Indoor ventilation
5>. Self-made thermostatic control box
6>. Equipment cabinet
7>. Air conditioning system
8>. Temperature control protection
11>. Water heater
13>. Hatch control
1>.It is a relay output mode and cannot be used as a power module. It cannot output voltage. The load needs to be connected to a separate power supply.
1>.1pcs XY-WT01 Digital Temperature Controller;
2>.1pcs 0.5meter NTC-10K B3950 sensor;
DC 6V-30V Wiring Diagram:
AC 220V Wiring Diagram:
1. Tested by ICStation's Outstanding Partner Onlykit:
(The language in the video is Russian)
2.Tested by ICStation's Outstanding Partner SYAVKA:
(The language in the video is Russian)
First we should say that ICStation doesn't accept any form of pay on delivery.Items used to be shipped after receiving the order info and payment.
1) Paypal Payment
PayPal is a secure and trusted payment processing service that allows you to shop online. PayPal can be used at icstation.com to purchase items by Credit Card (Visa, MasterCard, Discover, and American Express), Debit Card , or E-check (i.e. using your regular Bank Account).
We are PayPal Verified
2) West Union
We know that some of you do not have the Paypal account.
Bank Transfer / Wire Transfer / T/T payment methods are accepted for orders which the total price is up to US$500. The bank will charge about US$60 for the transfer fee if we do the payment in these ways.
For other payment method, please contact us at email@example.com for more details.
1. Yanwen / YunExpress / 4PX / China Post Airmail Service
(1) Due to the high risk of package lost recently, we have to stop using the free shipping way these days. Hope for your kind understanding! And the $5 is for tracking number and delivery insurance ^0^ Enjoy order from us.
Free Shipping for all orders over $20 ^0^ (with free tracking number and delivery insurance fee)
(2) Shipping time
Shipping time is 7-20 business days to most of countries; please view below table for exactly shipping time to your location.
7-15 working days to: Most of Asia countries
10-16 working days to: USA , Canada , Australia , UK , Most of Europe countries
13-20 working days to: Germany , Russia
18-25 working days to: France , Italy , Spain , South Africa
20-45 working days to: Brazil , Most of South America countries
2. DHL/FedEx Express
(1)Shipping Fee: Free for the order which meet the following requirements
Total price of the order >= 200USD or Total weight of the order >= 2.2KG
When the order meets to one of the above requirement, it will be shipped for FREE via EMS/DHL/UPS Express to below country.
Asia: Japan , South Korea , Mongolia . Malaysia , Singapore , Thailand , Vietnam , Cambodia , Indonesia , Philippines
Oceania: Australia , New Zealand , Papua New Guinea
Europe& America: Belgium, Britain, Denmark, Finland, Greece, Ireland, Italy, Luxembourg, Malta, Norway, Portugal, Switzerland, Germany, Sweden, France, Spain, USA, Austria, Canada
Note: Shipping Fee to other countries, please contact orders@ICStation.com
(2) Shipping Time & Delivery Time
Because the package would be returned to the sender if it had not been signed by the receiver , please pay attention to the arriving time of the package.
1) APO and PO Box Addresses
1) Delivery Time of mixed orders with items in different Shipping Status should be calculated using the longest estimate times listed.
2) Chinese Holiday Reminder: During annual Chinese holidays, services from certain suppliers and carriers may be affected, and delivery for orders placed around the following times may be delayed by 3 - 7 days: Chinese New Year; Chinese National Day,etc.
3) Once your order is shipped, you will receive an email notification from icstation.com
4) Track the order which with tracking number via below links: